ELK-SOL type heating cables can be used to protect the floors of cold rooms against heaving caused by frost. This is a cold room floor frost protection electric heater. The cable must cover the contact surface with the substrate and provide a thermal barrier to prevent lifting and other cracks. The power to be installed is around 20 to 40 W/m². Given the inaccessibility of the equipment and the cost of the work, we planned to double the circuit; the second cable constituting a possible recue. Of course, the two cables should never work simultaneously. The cable must be regulated by an electronic thermostat type ELTE-1 or ELTH-B390. The temperature sensor will be placed in a glove finger, in order to make it interchangeable, it will be arranged on the same plane and in the axis of the heating conductors.
Technical information on frost protection for pipes? Our engineers specializing in electric heating cables are at your service.
A price request for underfloor heating, electric heated floors or any other question...? Our sales department is at your disposal. Maintaining the temperature of industrial processes? We are listening to you
Contact us now at +33 1.64.62.04.40, all our technical, commercial and logistics teams are dedicated to you.Un renseignement technique sur de la mise hors gel de tuyauteries ? Nos ingénieurs spécialiste en câbles chauffants électriques sont à votre écoute.